Struvite control in Dewatering Centrifuge
Rockland County Sewer District #1, New York.
Effluent discharge system.
HydroFLOW Industrial Unit.
Struvite scale clogging the effluent discharge system of the wastewater treatment plant’s GEA Westfalia CA505 centrifuges.
Multiply the time between cleaning by a factor of two; from approximately once every two weeks to once every four weeks.
Reduce struvite scale accumulation in dewatering centrifuge effluent discharge.
- Dramatic scale reduction in the effluent collection discharge box.
- Very little to no scale accumulation observed on the previously scraped inspection section after thirty days of operation since the HydroFLOW unit was installed. Existing scale seems to be softening.
- The objective of extending the cleaning cycle from two to four weeks was met and greatly surpassed.
For the full case study please click on the PDF.