Inland Power Plant in China
Inland power plant in China.
Circulating Cooling System in Power Plant.
Two HydroFLOW custom 72” units.
River water - Quality of water varied from season to season. During summer raining reason, water turbidity was high.
Anti-scaling and biocide.
An Inland power plant in China using river water for the cooling system which has two of 600MW each. Chemicals dosage included anti-scaling and biocide. Refill water volume ran at 700T/hr.
Reduce chemical usage and improve steam condensation efficiency.
- Chemical dosage was eliminated for the operation.
- No hard scale was found inside the condenser and cooling tower cooling mate.
- Steam condenser transit temperature dropped by 1.5⁰C and vacuum pressure increased by 1KPa compared with the same period in previous year.
- Discharge water from the cooling tower was used now for gardening and other application because there were no chemicals in the discharged water.
For the full case study please click on the PDF.